Search the Community
Showing results for tags 'transmitter reading'.
Found 14 results
How to change encoder reading from positive to negative
automationtalk posted a topic in NJ Series / Sysmac StudioDoes anyone know how to change the reading on Omron servo motor reading from negative to positive? The encoder is reading negative values when it is moving in the forward direction. I am using 1S servo on NX1P2 controller on Sysmac studio software. Please suggest.
muhammadalisoenh posted a topic in CX-ProgrammerHai, I have problem with my CP1W TS001, suddenly reading result always #7FFE. i use CP1E-N60 and 2 expansion module, AD041 and TS001. I put TS001 after AD041 then my program code as follows : mov #8051 105 mov 7 D20 mov 8 D22 the reasult at D20 & D22 always #7FFE could someone help me to solve this problem?
Reading analog inputs from Chinese all in one PLC
Rajan_UAE posted a topic in MitsubishiHi All, I have a tiny Chinese controller all in one with 2 line text display. The documentation is not proper. GX Developer supports to program the devise. The devise is compatible to FX2N(C). Have any one in the forum used this type? I am not able to read its analog inputs AD0 and AD1 channels since I do not know which instruction I should use. I tries RD3A instruction but the PLC does not start. I attach a picture of the devise. Request support, Regards PLC-All-in-One-Text-Display-Domestic-Compatible-Mitsubishi-Op320-Industrial-Control-Board-10mt-Programmable-Controller.jpg_Q90.jpg_.webp
abdul_shaikh10 posted a topic in Modicon / Telemecanique / Schneider ElectricHey Guys, Hope you are doing well! Need all your experience support, to recover my existing project. As I'm at power plant project, we had PLC system with Vijeo Citect 7.3 licensed. As I'm newbie into this automation, doing my best to complete the project. AS I need you support to get resolved my project and my query. Query 1)Unable to get meter reading through plc to scada. Query 2)PLC gets and err blink and its not communicating as two plc available, one working perfect and other gives err blink after reset. Kindly help me out
password unlock tool
Rakesh. posted a topic in Mitsubishihi everyone i m traying to write to plc a program and getting this message then program is not downloading to plc 'there is a device in the program (main) that is outside of the range check the program and currect the device that outside of the range ' I m using mitsubishi fx3ga-60mt plc. please suggest me about it . thank you hello everyone please let me know about how to make software tool for password read from Mitsubishi,delta, omron, siemens plc . thank you
FX3U Stop Reading Channel Data
Sohail Riaz posted a topic in MitsubishiHello Everyone, Need help with reading channel data of FX2N-4AD with FX3U Cpu. I have added all the logic and it works also. Problem is that, FROM function stop reading/fetching data from FX2N-4AD after some time i.e couple of hours and value just hang. Like 502 or something, untill you reset the whole PLC. What could be the problem. For the further info, -I have connected the FX2N-4AD on the right of fX3U-64M. -There are two extension blocks FX2N-16EX and FX2N-16EYR also added to the right of FX3U-64M -Order of mounting....FX3U-64M > FX2N-16EX > FX2N-16EYR > FX2N-4AD > FX2N-4AD I have tried using the 2nd special module connected at the end, but It showed similar problem after few hours of running. THis shows that both Special blocks fx2n-4ad are okay. There is something wrong with PLC maybe? Please help
FX3U Analog Programming
markyspicer posted a topic in MitsubishiHi, Anyone can help how to program a analog coming from a level transmitter? I have 8 analog inputs (2 unit of FX3U-4AD) to be read out into the plc program. how can this be possible. I'm new to mitsubishi analog. it is different from my experience(using siemens before). Hope someone can help. Thanks!!! Marky
Pressure Transmitter Error
turboboy posted a topic in Allen Bradley / Rockwell AutomationHello Friends; Good day. I am working in oil and gas industry. I search the net but cannot find the allowable pressure transmitter % span error. I can not find any API or IEEE document in which the industry standards are mentioned regarding pressure transmitters upto 4000 PSIG and 1000 inches of water col. Please share your experience. Regards
CP1L connected with scanner symbol, with RS-232 on board CP1W-CIF01
FranciscoMYT posted a topic in CX-ProgrammerCP1L connected with scanner symbol DS-4308 reading 2D data matrix, with RS-232 on board CP1W-CIF01 Hi all, need some help because I can't read the information. Let me explain, I have a PLC, " CP1L-L14DR-D " with a RS-232 option borad " CP1W-CIF01 " , a scanner Symbol DS-4308, and I'm trying to read a data matrix 2d barcode (I don't know if that matters). so I build a cable with the next configuration, (one side male and the other female) PORT CONFIG PIN OUT SCANNER CABLE RJ-50 TO RS-232 PINOUT Maybe I'm missing a connection? a bridge? power supply ? ground? in the program, I only have this to check the communication, When my reception flag complete (A392.06), my instruction RXD is going to execcute, reading in D1500 the data. if is any error in communication (A392.04) or overflow (A392.07), my port is going to restart (A526.00) (ignore w0.03) with the followign config: (9600, 7,2,E, RS-232C, End code: Received Bytes 3 and I'm reading only, data on D1500 and D1501, and the data makes no sense. with the configuration of End Code: CR, LF, can't make it work, I read nothing. and if I change the END CODE: Received bytes to 4, don't work. and my flag A392.04 go to ON. PLC HAS 4 PIN SWITCH, ALL ARE OFF The configuration on the scanner is setting to default and then config to RS-232 Standard. So, what I'm missing? bad connections? plc don't support? scanner config? program?
Temperature Transmitter Configurations
applecruncher1 posted a topic in General Topics - The LoungeHi, Recently, we replaced our old digital temperature transmitter with a Baumer Flextop 2201 digital temp transmitter. The application of the digital temp transmitter is for a hydraulic press and the output is fed to the Siemens S95-U plc. The Flextop was able to react properly promptly when there is increase in temperature but whenever there are sudden drops in temperature it is slow to react. The analog transmitter (dial) was already at 25 C when the hydraulic press was shut down while the Flextop was still at 35 C. We used a three wire configuration for this. Does this have to do with our wire configuration? I know there are 2 wire ,3 wire, and 4 wire configurations for 4-20 ma sensors but I'm not sure what are their differences among them. Please see attached configurations below. Thanks,
Temperature measurement using Arduino Nano, RTD PT100 temperature sensor and 4-20 mA transmitter
Absolutelyautomation posted a file in Other PLC Demo Software
[Other PLC Demo Software] - Temperature measurement using Arduino Nano, RTD PT100 temperature sensor and 4-20 mA transmitter
Absolutelyautomation posted a topic in Download CommentsView File Temperature measurement using Arduino Nano, RTD PT100 temperature sensor and 4-20 mA transmitter Temperature measurement usind Arduino Nano, RTD PT100 sensor, 4-20 mA current loop transmiter, and a python app for visualization Submitter Absolutelyautomation Submitted 04/01/16 Category Other PLC Demo Software
CP1E-N40 + CP1W-TS102
arrowsmith74 posted a topic in OmronHi ! I have a question regarding the handling of the signal from the TS102 connected to my PLC. I downloaded a .pdf LINKED from "my omron", read it and put together a small program just to test the expansion unit and sensors. But I cant get any readings from the sensors and can't figure out why. I have never used a TS102 expansion unit before and would be glad if someone have an idea of what I'm doing wrong. Everything is brand new, so I'm quite sure I am the problem here..... If someone have an answer and maybe even an programming example to upload I would really appreciate it. Best Regards! PT100 sensor test 3.cxp
Simulation in Foundation Fieldbus
joshi171 posted a topic in SiemensHi Guys, Did anyone performed the process value simulation of Rosemount 5300 Level Transmitter (FF Communication) using Emerson 475 communicator? The simulation jumper is not available physically on the device. The only simulation option in the hand held communicator available in the following path. Configure>>Manual Setup>>Classic View>>Advanced Transducer Block>>Parameters1.. But that option too is highlighted and not editable. Can anybody help me how to simulate the value from device so that I can check in my host DCS (Siemens PCS7). Thanks in Advance, GJ