Search the Community
Showing results for tags 'fail'.
Found 4 results
I am investigating a failure that occurred... We have a L62 Processor with RIO and Redundancy, it was reported that a system "failed to stop" this system is started and stopped via outputs channels on an OW16I card on one of the RIO racks. Has anyone had experience an issue with IO not responding as it should if the redundant partner is disqualified? Also, there was a know network issue and the main Ethernet card (Slot 1) did have a communication issue (not the same Ethernet card for the RIO (Slot 3).
We have an install base of about 120 TWIDO PLCs anywhere from 1 to 10 years old with varying configurations, but all using the TWDLCAE40DRF base unit. Lately (over the past couple of years), we've had multiple instances where upon power being removed from the device, and then turned back on, the base unit fails and will not power back up. The typical case is that we turn on the power, a couple of LEDs flash for a brief (< 1 Sec) moment, and then nothing - unit is dead. Just wondering if anyone else has encountered the same thing.
Hello good morning, I would like to comment on a case, I have a MR JE A 20 driver, it is connected to a plc and it moves a clamp. The fact is that I have variations of distance until it reaches stops and skips the inverter by overload. Well my question is the following, I want to use the mr configurator, I downloaded it, but it gives me a drawback when I connect it I figure as the driver, but in the program it only appears offline, I can not revert, it will be because the Plc Thank you very much for your reply