Search the Community
Showing results for tags 'ge cimplicity'.
Found 2 results
I am Facing Problem Getting Kwh Readings From My Satec MFM(PM130-PLUS), Required for an easy & reliable Monitoring On Energy Consumption . Connected via RTU Slave Interface with SCADA User Interface (GE_Cimplicity). Here's what happening : Actual Kwh Reading has 8_decimal data digits on MFM LED Display but on Cimplicity SCADA User Interface Screen It only able to Display it as 4_Decimals point digit, eg, 63290058 kwh shows as 0058 , and 15299999 kwh shows as 9999 , and then 15300001 kwh shows as 0001 i.e 1 only! Plz Do a Rply , your slight approach to my Query Will be highly Appreciated!! :)
Hi Guys, I am new to Cimplicity SCADA but I was familiar with HMI. Now my requirement is to separate / dedicate the alarms to each process or setup in the respective screen. Prior they have made all alarms to fire on all screens/ all process. Now idea to separate the alarms in the respective screen. In all screens on top, if I click on alarm object, its properties are Link Container and it has Link source file as xxx.cim and Link source Object as Alarm. Please guide me from the beginning, how they configured the existing alarms also I am not understanding. I need help please. Thanks a lot.