Search the Community
Showing results for tags 'triggers'.
Found 2 results
Hi all, 1. I'm working on alarms in FT view ME with rslogix 500. I have seen all the alarms in my plc program are kept in the N7:1 and N7:3 out of which all bits for N7:1 is used and 9 bits for N7:3 is used. So right now I'm creating the alarms messages for N7:1 I went and created tag with name ALARM1 digital bit and used the device address as ::[shortcut]N7:1/1 and then used the same alarm tag while creating alarms and kept trigger value as 1. But while reading some post, few of them has mentioned to use L16 L32 in address bit ::[shortcut]N7:1(L16) Can't I use this ::[shortcut]N7:1/1 ? 2. Basically I'm converting pv550 to pv700. So I went and check alarms in pv550 in panelview 32 and I have seen there we have use "ack tag" as N7:2. because in plc program it was mentioned in description of N7:2 as ALARM RESET ADDRESS ARRAY. DO I have to use this N7:2 in acknowledging the alarms. Please some one help me
haylow_89 posted a topic in Allen BradleyI have entered the messages many times into the Alarm Setup but every time i re-open the alarm setup, every message that has the Trigger Value=1 will be deleted. Anyone have a similar issue?