Search the Community
Showing results for tags 'nx102'.
Found 4 results
We have a customer insisting on communicating with our NX102-9000 over EtherCAT, we have explained multiple times that EtherCAT is not intended as a facility communication protocol and recommended that instead they use Ethernet/IP, but after a year of pushing back they are still insisting and willing to pay for the Engineering work to get this to happen. Has anyone successfully configured two EtherCAT masters to communicate with each other? In the past I have used the PN-PN Master Coupler from Siemens to get two ProfiNet Masters to communicate with each other so I am hopeful that a similar device exists for EtherCAT, but I have not had any luck searching the web for such a device. Does anyone have experience with or know of such a device? Thank you!!
Omron NX102 / NX1P2 cannot trigger MOXA ioLogik E1212 Outputs through Ethernet/IP connection, But I can read the Inputs Status All the time. Just CANNOT trigger the Outputs signal through Omron PLC. Moxa claim that they can use AB PLC trigger E1212 outputs and no problem at all, but now OMRON PLC cannot. Steps I am doing... Define the custom Data Type Structure. Create a variables with custom data type. Mapping with MOXA eds file setting. Inputs - 67 bytes, Outputs - 1 bytes. I had Install the MOXA EDS file I do contact MOXA Support channel, they claim that Omron PLC not response to port 2222 . Can anybody help ? because same Omron PLC using for test also tested with other EIP device with no problem at all. I have no idea which party are problem now... T.T
AngryRobot posted a topic in NJ Series / Sysmac StudioIs it possible to setup Ethercat parameters from within the PLC program? I am facing a situation where a machine is going to have changeable tooling fixtures and each fixture is going to have an EtherCAT device on it. I am guessing they will need to be setup to look like the same node to the PLC, but they will have different physical IDs and different settings for some of the parameter fields. They will be the same device so they will have the same parameter fields, just different values in those fields. I can also get these devices with EthernetIP as the fieldbus option. In that case I would always have a network error because the PLC would always see one of the devices missing from the network. is it possible to enable/disable Ethernet connections from within the program logic to avoid the error?
Hi. We are struggling a bit with the analog IO on the EIC202 coupler. Have tried tag sets, and gotten the digital IO to work without problems, but not the analog. Any tips here? We are using 2x NX102 with 1x ID4442, 1x OD4256, and 2x EIC202 with 1x ID4442, 1x OD4256, 1x AD2603, 1x DA2603 on each, for a redundancy-system. Software is Sysmac Studio. EIP connection.