Search the Community
Showing results for tags 'cpe330'.
Found 1 result
Genew posted a topic in GEHi, I have been helping a client overseas to upgrade and install some CPE330 PLCs configured as CRU320s to replace their faulty CRU320s. They had been previous controlling primarily from the Secondary (PLC B) for the last 6 years or so until PLC B finally failed due to a power surge. Having configured and downloading the previously working project to the PLCs in their respective hardware configuration, the system refuses to allow PLC A to control via the Citect SCADA, despite showing as Active and Ready on both Citect and the RMX Modules, although no outputs are read through Citect when PLC B is switched off at all. I found this forum from searching a previous post about drivers and if 90-30 and Rx3i required any changes (their previous setup before being Rx3i was 90-30), but as you confirmed in that thread, that the driver should be fine, unless you know of any issues with it working alongside newer PLCs configured as older ones? I should note we have discovered that the firmware revisions on each PLC is different and will be getting them to upgrade the later one to coincide. Each PLC has been tested in either HWC and both operate when configured as PLC B and neither operate fully as PLC A. We've had a GE technician check over the project and extracted text files from the PLCs and has confirmed the code and config looks correct. We're running out of ideas and out next step is to try and borrow 2 PLC racks and try to run them all first hand to see if PLC A runs on the SCADA in our office to try and rule out the software altogether! Any help you can provide would be much appreciated, Gene