Search the Community
Showing results for tags 'cards'.
Found 3 results
For Sale: Siemens ET200SP Hardware - New in Box
RVaughan posted a topic in For Sale, Employment, Services or WantedInput cards, DI8x24VDC BA, 6ES7 131-6BF01-0AA0, NEW in box ,quantity 10 IO-Link CD-Master 4SI SIRIUS, 3RK1 005-0LB00-0AA0, NEW in box, quantity 4 IO-Link Master 4SI IO-Link, 6ES7 138-4GA50-0AB0, NEW in box, quantity 3 IO-Link Communication Module, CM 4xIO-Link, 6ES7 137-6BD00-0AB0, NEW in box, quantity 1 CM AS-Master ST, 3RK7 137-6SA00-0BC1, New in box, quantity 1 Located in USA. Make offer, shipping included. Pictures available on request, send email address in a PM.
Hi friends , recently i ve been doing some diggings about remote IO cards, in my factory we have a CJ2m PLC and it communicates with remote IO cards with four numbered words (2080.00 , 2080.01, 2080.02....2080.15 ) and there were several dip switches on the IO cards, which were set but i can't understand what was the basis of that settings. So I'd like to know how these dip switches behave and what are the uses of them ?? and how is it possible to have 4 numbered word bits ?? pls help me someone to clarify this, i tried internet, but cudnt help myself !!! thank you Here I attach one of the pictures i took of one of the remote input cards.
Replacing compactLogix analog cards
madatix posted a topic in Allen Bradley / Rockwell AutomationHello everyone, we have two damaged analog cards for CompactLogix PLC ( 1769-OF8C & 1769-IF8) that we are going to replace. my experience is with Siemens and Schneider PLC's but for Allen Bradley, not so much so my question is : are there any requirements or specification other than the part-number that could prevent the cards from going in service directly ? as for the firmware, series and so on ? and do i need to do any extra work after replacing the card ? thank you Best Regards