Search the Community
Showing results for tags '33:17075'.
Found 2 results
Hi there. Recently I've experienced problems when connecting to a S7-300 PLC via MPI/PROFIBUS. I use a PG with CP5711 processor. The thing is that I'm able to connect when I plug the 6ES7901-0BF00-0AA0 cable (male to male) directly to the PLC connector, but when I try to do connect to a PLC that has any device connected to the DP port (let´s say an inverter or HMI) I get 33:17075 error. PG/PC Interface it's correct, in fact another PG with the same configuration is able to connect through the already connected DP device's cable. Station number and transmission rate is all correct. So I tried the Simatic NET Diagnostics Test and I got error 0x0313 and since the mentioned parameters are correct I refered to this link: How do Diagnostics and Remedy work in STEP 7 when an online connection with the CP... - ID: 11492532 - Industry Support Siemens Where they say the following: I've searched for this readme file but can't find it, and there are no useful results when looking for it on internet. Why am I able to connect directly to the PLC but not when another device is connected and I have to use the female connector of the DP connector itself? Should I try to reinstall CP5711 drivers? According to Windows, I got the last drivers for the CP. Thanks in advance and I hope you can help me!
hi all, I have CPU 315 - 2 DP. I can't download program from S7 manager to CPU. I have message Help on Message 33:17075 Description: All stations on this subnet must have the same value for the transmission rate. The interrupt may not be assigned for other hardware components. The MPI addresses in the network must be unique, meaning each address may only be assigned once. The local Station address must also not be greater than the highest station address in the programmable controller. Remedy: Call the program "Setting the PG/PC Interface" in the Control Panel. Under "Properties" set the transmission rate used in the network and adjust the local node address to match your network. Set a station address for your programming device/PC which is not higher than the highest station address in the network. Shorten your HSA address to match the PROFIBUS addresses of the slaves used. i put all the interface setting PC/PG on default but i've the same message. what i must do ? please some help.