Search the Community
Showing results for tags ' vhsc24'.
Found 3 results
Vinicius Santos posted a topic in Allen Bradley / Rockwell AutomationHello guys, I am running an application for packaging measurement using a sick DFS60B incremental encoder (programmable from 1 to 10000 PPR). In more detail, it passes packaging on a conveyor belt and we have created an inspection station and an expulsion station (defective packaging), so we use the encoder to check at specific points of the packaging for defects (we use special sensors to check defects). ) (there are four in total). However, the problem we are having is the following: When reading the encoder in the PLC, the same means that performs "jumps" and does not enter the windows (GRT and LES) created on the ladder, ie, as if it were not continuous. . I understand that because the VHSC24 card works at 1 MHz in counter mode, this type of problem should not occur according to our application is not even 100 KHz. For example, our case: Using 1000 PPR and the motor speed (coupling output) is 3600 RPM (in practice it is around 1750 RPM) the frequency is calculated as follows: F = (PPR X RPM) / 60. : F = (1000x3600) / 60 = 60 KHz, ie 60 KHz is much less than 1 MHz, I think this kind of problem does not occur. Application Info: . Studio 5000 V31 . PLC Model: Rockwell 1769 - L19ER-BB1B CompactLogix 5370 . Encoder Card: 1734-VHSC24 / C . Incremental Encoder: Sick, DFS60 up to 10,000 PPR and HTL Electrical Interface. Using a 200 mm circumference / perimeter wheel. . Motor Nameplate Data: 1670 RPM, 0.37 kW / 0.5 HP, 60 Hz . Inverter: Weg CFW500, Output Frequency 62 Hz. Card Settings we use RPI: 2 ms Type: Counter, but we already use it as Encoder X1 Store Count Mode: Disabled Filter: No Filter, but we use 50 KHz and 5 Khz filters in our tests. Counter Attenuator: 1 Wiring Diagram VHSC24 We turn on encoder A at input 0 and encoder Aret at input 1 In logic (Structured Text) Using the PMUL instruction to convert encoder (Pulse) data to mm scale. (Ladder) The window comparisons part (GRT and Les) and other part of the process. We emphasize that we performed the tests also only with the reading and comparison part of the data, excluding the other parts, precisely to verify the issue of Scan, but the problem persisted. If anyone here in the forum has some information that can help us, I would appreciate it.
Jiggadoo posted a topic in Allen Bradley / Rockwell AutomationHello! I have a problem with Allen-Bradley High Speed Counter card 1734-VHSC24/C. I need to make changes to the configuration parameter .OnValue1 (DINT) during the system is running. Now, for changing the parameter value, I need to switch off the module and this can not be done during the line is running. I think that maybe this can be done using the explicit messaging. I could not find information for this from internet, so now I ask you to help me with this item. If anyone have experience or knowledge of this, please help me. I do no have experience using explicit messaging. My configuration: Studio 5000 Logix Designer V24.00, 1756-L71S V24.11, Ethernet/IP, 1734AENTR, 1734-VHSC24/C countermodule.
Hi all, I am taking a Kubler draw wire encoder back to a 1734-VHSC24 and having a little bit of an issue with the rollover. With the draw wire untouched the output value seems to be fluctuating over time and appears to be drifting backwards to the rollover value making our distance measurements completely useless. Does anyone have any insight as to why that might be?