Cx-Programmer & NB-Designer
Posted 15 August 2013 - 01:22 PM
I have a CP1L-E and NB, and I can not make the communication between the two.
The question is, CX-Progammer is necessary to say that there is a NB?
For the NB gives this error (PLC Response Error)
Thanks a lot
Posted 15 August 2013 - 09:44 PM
The serial port defaults to Host Link, 9600, 7,2,E.
Edited by BobB, 15 August 2013 - 09:48 PM.
Posted 16 August 2013 - 04:55 AM
Posted 16 August 2013 - 03:26 PM
Posted 16 August 2013 - 04:33 PM
My last post was for a serial connection.
Yes, if you want to use the Ethernet port it will have to be FINS/TCP connection.
The PLC defaults to 192.168.250.1.
Posted 16 August 2013 - 08:22 PM
I don't understand why Omron brought out new models that don't support Ethernet IP like the CJ2M does. I wish they would settle on one protocol and stick with it!!
Posted 16 August 2013 - 10:19 PM
It is annoying that they do not do the same think all the time. May have something to do with marketing?
Posted 16 August 2013 - 10:31 PM
I wish they would settle on one protocol and stick with it!!
All of the Ethernet and EtherNet/IP ports support The FINS protocol.
Posted 18 August 2013 - 11:55 AM
Posted 18 August 2013 - 12:47 PM
I am well aware of the model structure. My gripe is that no two models have exactly the same Ethernet configuration! It seems like Omron should be consistent between models.
Mendon, the CP is a lower model CPU than the CJ, so it does not have all the same capabilities.
The CP1IL-E (or better yet CP1H-E) would be an excellent solution to the notably missing remote I/O on the CJ2 IF it supported tag based data links.
Yes, I know it can be done with FINS, but it is a real PITA to do it!!
0 user(s) are reading this topic
0 members, 0 guests, 0 anonymous users