Search the Community
Showing results for tags 'ul508a'.
Found 1 result
Hi All, I am pretty new at electrical design for PLC control panels. We are a UL508A shop, so this is the code I refer to most. Something struck me as odd when I was trying to size wire for this control panel. UL508A 28.3.1 says this: The required size of the field wiring terminal shall not be less than 14 AWG (2.1 mm2) and shall be determined by: a) Calculating the required ampacity per 28.3.2 – 28.3.6; and b) Determining the minimum field wiring conductor size from Table 28.1 having a corresponding ampacity that is equal to or greater than the required ampacity from (a). How can the minimum wire size be #14 AWG? We use #16 AWG for wire to the PLC modules? Are we breaking code or is there something I am missing? Also, understanding code books can be difficult. Is there a website or place I can go to get a plain English translation? I feel like I will read a sentence over and over again to try to understand what they are saying, and feel like there's is a much easier way to say it than the way it is written. For example, "28.3.1 b" ……...what is it really saying?