Search the Community
Showing results for tags 'points'.
Found 4 results
I am trying to export the Modbus points lists from a DAServer in Archestra SMC but I am getting an error message shown in the attached image. All options are greyed out and I cannot export the points list from the PLC node. I know there are points configured on the PLC node because data is updating the the InTouch application. Any help you can provide is greatly appreciated!
I am Facing Problem Getting Kwh Readings From My Satec MFM(PM130-PLUS), Required for an easy & reliable Monitoring On Energy Consumption . Connected via RTU Slave Interface with SCADA User Interface (GE_Cimplicity). Here's what happening : Actual Kwh Reading has 8_decimal data digits on MFM LED Display but on Cimplicity SCADA User Interface Screen It only able to Display it as 4_Decimals point digit, eg, 63290058 kwh shows as 0058 , and 15299999 kwh shows as 9999 , and then 15300001 kwh shows as 0001 i.e 1 only! Plz Do a Rply , your slight approach to my Query Will be highly Appreciated!! :)
Hello everyone! First of all, I'm a new comer to this forum from Indonesia. The name's Inno. Looking forward to share knowledge with all of you So I had this trivial, but annoying matter with CX-Supervisor Text Points. I had connected it to NJ101 controller. There I made a sample STRING, let's say "1234". I set this STRING to be stored in D0 memory, which means in ASCII it'll now contains : D0 = #3132 D1 = #3334 Then I use the Display Value (Text) Action to a Text Object in CX-Supervisor. The problem is, each Word on the Point display the LSByte first. So the resulting view in CX-Supervisor is : "2143", while I expect to see "1234" I know this can be easily solved by swapping the bytes inside the NJ program, but I'm curious, does CX-Supervisor has the feature to swap these bytes automatically? I mean, even NS or NB HMI can do so to accomodate Mitsubishi/others String system :D This occured for any Text type I choose (Signed/Unsigned/Raw Binary). Waiting for your suggestions