Search the Community
Showing results for tags 'cards'.
Found 2 results
Hi friends , recently i ve been doing some diggings about remote IO cards, in my factory we have a CJ2m PLC and it communicates with remote IO cards with four numbered words (2080.00 , 2080.01, 2080.02....2080.15 ) and there were several dip switches on the IO cards, which were set but i can't understand what was the basis of that settings. So I'd like to know how these dip switches behave and what are the uses of them ?? and how is it possible to have 4 numbered word bits ?? pls help me someone to clarify this, i tried internet, but cudnt help myself !!! thank you Here I attach one of the pictures i took of one of the remote input cards.
Hello everyone, we have two damaged analog cards for CompactLogix PLC ( 1769-OF8C & 1769-IF8) that we are going to replace. my experience is with Siemens and Schneider PLC's but for Allen Bradley, not so much so my question is : are there any requirements or specification other than the part-number that could prevent the cards from going in service directly ? as for the firmware, series and so on ? and do i need to do any extra work after replacing the card ? thank you Best Regards